Electric Cabinet Switchgear (HXGV1(XCN58)-12)
|FOB Price:||Get Latest Price|
|Min. Order:||1 Piece|
|Payment Terms:||L/C, T/T, Western Union|
- Model NO.: HXGV1(XCN58)-12
- Structure: Protection
- Form: Partly-welded Type
- Size: 3 Uint
- Shell Material: Stainless Steel
- Brand: Ville
- Trademark: VILLE INDUSTRY
- Specification: IEC CE, ISO
- HS Code: 85
- Type: Power
- Certification: ISO9001:2000, CCC
- Operation Voltage: High Voltage
- Application Range: Power Plants
- Shell Protection Grade: IP55
- Rated Voltage: 10kv
- Transport Package: Wooden Cases
- Origin: Ningbo China
HXGV1(XCN58)-12 SF6 Ring Main Unit Switchgear (hereafter referred to as Switchgear) is designed and manufactured by ourselves according to the requirement of the power supply in our country.
As a new generation of Indoor 10kV electric appliances, by pattern test and commissioning, whose performance index is up to IEC298 [AC Metal-clad Switchgear] standard and relevant national standard. It is light in weight, easily operated, safe in usage, high reliability, independent of environment and free from maintenance etc.
The switchgear is a combined electric appliance that sealing each main circuit switch into a metal enclosure, use SF6 gas as arc extinguishing and insulation media, suitable for ring main power supply and double radiation power supply in 10kV middle voltage power supply network, use as terminal power supply as well.
The product is suitable for power distribution and control in mines, residential district, schools, parks ect, due to enhancing the reliability of power supply by ring main power supply.
In addition, with the character of easily wiring, small size, convenient installation, it is suitable for being installed in the Combination Substation as primary side HV equipment.
A. Ring main unit is composed of three compartments. The load switch is laid in the sealed cubicle welded by stainless steel plate. There is SF6 gas of 0.04Mpa as the medium of extinction and insulation.
B. There are three positions, namely closing, isolating, earthing separately, whose positions are determined by the indicator on the mechanism panel.
C. The cable incoming/outgoing line uses cable connector (plug ins).
D. There is a separate operation mechanism in each compartment, where you can realize manual operation and manual and motor operation. There are closing/opening indication on the operation panel.
E. The fuse is installed in the epoxy resin tube in the middle of the cubicle. Due to the needle type mechanism of fuse and the opening device of operation mechanism in load switch are connected together, once the fuse is blew out with fault, the tripping mechanism will make the load switch opening.
F. The load switch apply revolving extinction arc principle, which will make contact long life endurance.
G. There is manometer in the front of the switchgear to monitor the pressure of the SF6 gas.
H. In order to prevent the inner of equipment from hyperbaria with circuit fault, there is a pressure release device at the bottom of the switchgear.
Please provide the following data:
A. Name, specification, type, quantity, delivery date of product, rated voltage of fuse;
B. Pareto diagrams and layout plan of RMU;
C. Spare parts needed such as charging/discharging device;
D. Cubicle color;
E. Any special request can be settled by negotiation
--From the very beginning, VILLE ensures quality in every step to achieve the best quality.
--With more than 30 years' experience in power industry, VILLE brings you an optimized solution.
--Wherever you are, VILLE global network will support and provide you with value.
--In response to your needs without delay, VILLE knows the value of your time.
Packaging Details: The accessories packed in plywood cases,the main body in nude.
Our Best Service For You
1. Pre sale service
A. Make technical solution
B. Send quotation, technical data sheet and drawing
C. Prepare power transmission plan, testing plan,and shipment plan
2. In sale service
A. Supervise the manufacturing schedule totally in accordance with the plan
B. Send photos to customer during every manufacturing process(hold point)
C. Inform the customer one week before testinng.
3. After sale service
A. Installation and commissioning, training the workers
B. Quick response within 12 hours any time
C. Provide 12 months gurantee period normally.