Xgn56-12 (XGT3-12) Cubicle Fixed AC Metal-Clad Switchgear
|FOB Price:||Get Latest Price|
|Min. Order:||1 Piece|
|Production Capacity:||50000 Sets/Year|
|Payment Terms:||L/C, T/T|
- Model NO.: XGN56-12 (XGT3-12)
- Warranty: 1 Year
- Connection Mode: Series Switching Power Supply
- Power Supplying System: Terminal Power Distribution Equipment
- Rated Frequency: 50Hz
- Lighting Impulse Withstand Voltage: 75
- Trademark: VILLE INDUSTRY
- Specification: IEC Standard
- HS Code: 85
- Output Type: Multiple
- Input Voltage: 12kv
- Voltage Regulating Mode: Frequency Modulation Type
- Rated Voltage: 12kv
- Rated 1min Power Frequency Withstand Vol: 42
- Degree of Protection: IP3X
- Transport Package: Wooden Case or as Per Requirement
- Origin: Ningbo China
XGN56-12 (XGT3-12) Cubicle Fixed AC Metal-clad Switchgear (following abbreviation switchgear) is a lastest version of high voltage electrical complete set of equipment which designed and developed by self, it fits national standard GB3906 " 3-35kV's AC metal switchgear" and power ministry requirement of DL 404 "indoor AC HV switchgear's technology requirement of order", and also satisfied requirement of international standard IEC 298 " AC metal sealed switchgear and control equipment which rated voltage is 1kV to 52kV", and possesses the ability of " five guards against" required by two ministries.
This product has absorbed the advanced technology of abroad, and design and develop by self according to the question of higher accident rate in running and large volume at present the same's switchgear of our country occurs, and it posses the merits of small volume, only 50% with ordinary switchgear volume, high reliability, good capability, "five guards against" interlocking mechanism is reliable and simple etc.
The switchgear is suitable in indoor complete set of device which 3.6~12kV three-phase AC 50Hz single-bus burst, it used as electric energy accepting and distributing and possess the merit of control and protects and monitoring to the circuit etc. It can be used in all kinds of power plant and power station industrial and mining enterprises, high-rise building, etc. And can also be used in open and close place with RMU.
|Rated Voltage (kV)||12|
|Rated Insulation Level||Rated 1min power frequency withstand voltage||42|
|Lighting impulse withstand voltage||75|
|Main Busbar Rated Current||630||1250||2000 2500 3150|
|Branch Busbar Rated Current||630||1000 1250||2000 2500 3150|
|4s Rated short-time withstand current (r.m.s.) (kA/s)||20||31.5||40|
|Rated Peak Withstand Current||50||80||100|
|Degree of protection||IP3X|
|Dimensions (Width×Depth×Height) mm||900×1050×2300||1050×1050×2300|
Please provide the followings
A. Main wiring scheme code, single line system diagram, pareto diagram and layout plan.
B. Secondary principle diagram, terminal pareto diagram. If without it, conform with the manufacturer's terminal pareto diagram.
C. The type, specification and quantity of the electrical components of switchgear.
D. Summary table of electrical equipment.
E. Please provide span and height dimensions if busbar bridge(between two ranks of switchgear or between switchgear and wall) is needed.
F. Please indicate if switchgear shall be on the special condition.
G. Please indicate type and quantity of other accessories, if necessary.